Question about Heating & Cooling
Remove cover on your stat using a small wire not touching the ends jump red-power to yellow compressor should start red to green fan should come on im assuming the installer used the most common wire configurations these test can also be peformed at the inside the furnace remember 24volts is present sounds like your thermostat is bad easy to determine using the test i mentioned good luck
Posted on Aug 21, 2010
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 25, 2015 | Frigidaire Heating & Cooling
on Sep 02, 2010 | Heating & Cooling
Jun 11, 2011 | Carrier 38CKC036 Air Conditioner
Aug 17, 2009 | LG Heat cool Window Air Conditioner
Jul 30, 2009 | Heating & Cooling
Jun 30, 2009 | Dometic Rooftop RV Air Conditioner
Jun 11, 2009 | 1997 Dodge Caravan
Jul 18, 2008 | Heating & Cooling
37 people viewed this question
Usually answered in minutes!