Question about MSY-A17NA Air Conditioner
Hello Sounds like a restriction/clog if the unit is (pumping down) .try adding freon when the compressor cools off & starts again.See if the low side #s improve.Make sure the service valves are open.
Posted on Aug 20, 2010
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 22, 2014 | Honeywell Electronic Programmable...
Feb 03, 2014 | Midea Heating & Cooling
Nov 16, 2013 | Heating & Cooling
Sep 03, 2010 | Heating & Cooling
Aug 21, 2009 | Sanyo Split System Air Conditioner
Jul 26, 2009 | Ruud UBHC Air Conditioner
Dec 14, 2008 | Hitachi RAS-09UH Air Conditioner
Nov 02, 2008 | Ruud UAMB Air Conditioner
Apr 22, 2008 | LG LSC091PMA Split System Air Conditioner
114 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: