Question about Teledyne Laars Laars Lite 2 Pool Heater 325,000 Btu / Natural Gas
Thank you for posting your question here on Fixya.com.
First you will need to get a hold of a digital or analog multimeter and set it for the lowest range of Ohms you can. Your safety circuit is a string of several switches all strung together in a row with the gas valve at the end and the beginning of said string. Any one switch being open or a bad connection anywhere in the circuit and the heater will not fire.
You task is to remove one end of the circuit from the valves TH or TT post and put one end of you meter on that wire and the other end on the TH/PP terminal. It will likely read infinite resistance. Leave one meter lead where it is and remove the other. Follow the circuit from the connected lead up to the first switch. Check continuity from the lead left connected to both sides of the switch. If there is continuity to both sides the switch is fine. Keep moving from switch to switch until you find the bad switch or connection. There may be more than one. When the circuit is working properly and there is nothing within the heater to cause it to shut off you should have 5 ohms or less across the entire circuit. Once you get the reading to that level the heater will work as it should
If you are not familiar with the process I described you would be better served hiring a pool technician to perform this repair as you can cause significant damage to the heater if you do not repair it properly.
If this answer does not fix your problem, please comment with additional details prior to rating the answer. Positive feedback is appreciated once your problem is solved!
Posted on Aug 19, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Oct 09, 2012 | Lite On Laars Lite 2 Heaters: 250,000BTU...
Sep 14, 2010 | Teledyne Laars Laars Lite 2 Pool Heater...
Jun 13, 2010 | Lite On Laars Lite 2 Heaters: 250,000BTU...
May 07, 2010 | Teledyne Laars Laars Lite 2 Pool Heater...
Jun 07, 2009 | Teledyne Laars Laars Lite 2 Pool Heater...
Aug 31, 2008 | Lite On Laars Lite 2 Heaters: 250,000BTU...
79 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: