Question about Goodman CKL60AR60 Air Conditioner
The orifice is the metering device inside the evaporator coil and comes installed from the factory in the coil itself. Some condensers do come with orifices taped to the side of the unit, but they only do that to ensure you have the right size orifice. Sometimes you will have a 3 ton evaporator and a 2.5 ton condenser. In this case you want to change the orifice so that it meters the refrigerant correctly. But if you have a 3 ton condenser and a 3 ton coil, which is normal, you don't have to do anything. So to answer your question, your coil already came with a orifice inside and nothing needs to be done unless there are two different sized units as described above. Hope I didn't bore you too much and helped you with your question!
Posted on Aug 19, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 26, 2015 | Heating & Cooling
on Dec 29, 2009 | Heating & Cooling
Jan 11, 2015 | Heating & Cooling
Apr 20, 2014 | Sanyo Split System Air Conditioner
Jul 22, 2011 | Goodman CKL36AR36 Air Conditioner
Jan 02, 2011 | Goodman CLJ30AR32 Air Conditioner
Dec 26, 2010 | Fujitsu Heating & Cooling
Jun 07, 2010 | Goodman CLQ36AR49 Air Conditioner
Oct 06, 2009 | Heating & Cooling
Sep 09, 2007 | Ruud UAMB Air Conditioner
149 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: