Question about Heating & Cooling
"Y" terminal at the stat feeds condensing unit outside, common from the condensing unit to common on the furnace transformer.
"G" terminal on the stat brings the fan on for air circulation. In cooling mode "Y" terminal also brings the fan on. If this furnace was not A/C ready check the VA capacity of the transformer. Should be about 40VA. Make sure there is a fan relay to bring the fan on in the cooling mode.
Posted on May 01, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 03, 2014 | Goodman Manufacturing Goodman GMH81205DX...
Jan 08, 2013 | Heating & Cooling
Oct 06, 2012 | Goodman Manufacturing GMH950453BX - 45,000...
Oct 26, 2011 | Goodman CKL24AR24 Air Conditioner
Apr 07, 2011 | Heating & Cooling
Feb 16, 2011 | Heating & Cooling
Dec 11, 2009 | Goodman Heating & Cooling
Aug 18, 2009 | Goodman CLJ30AR32 Air Conditioner
Dec 05, 2008 | Goodman Heating & Cooling
163 people viewed this question
Usually answered in minutes!