Question about Heating & Cooling
"Y" terminal at the stat feeds condensing unit outside, common from the condensing unit to common on the furnace transformer.
"G" terminal on the stat brings the fan on for air circulation. In cooling mode "Y" terminal also brings the fan on. If this furnace was not A/C ready check the VA capacity of the transformer. Should be about 40VA. Make sure there is a fan relay to bring the fan on in the cooling mode.
Posted on May 01, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 06, 2013 | ICM286 Furnace Control Board
Jan 08, 2013 | Heating & Cooling
Jan 27, 2011 | Goodman GDS80904BNA Open Flame Heater
Oct 02, 2010 | Goodman GMS90703BXA Heater
May 14, 2010 | Goodman GMS90703BXA Heater
Jan 06, 2010 | Goodman Heating & Cooling
Dec 11, 2009 | Goodman Heating & Cooling
Jun 02, 2009 | Goodman GMS90703BXA Heater
Nov 23, 2008 | Goodman GMS90703BXA Heater
Jan 07, 2008 | Goodman GMS90703BXA Heater
163 people viewed this question
Usually answered in minutes!