Question about Air Conditioners
"Y" terminal at the stat feeds condensing unit outside, common from the condensing unit to common on the furnace transformer.
"G" terminal on the stat brings the fan on for air circulation. In cooling mode "Y" terminal also brings the fan on. If this furnace was not A/C ready check the VA capacity of the transformer. Should be about 40VA. Make sure there is a fan relay to bring the fan on in the cooling mode.
Posted on May 01, 2008
Tips for a great answer:
Nov 03, 2014 | Goodman Manufacturing Goodman GMH81205DX...
Jan 08, 2013 | Air Conditioners
Oct 06, 2012 | Goodman Manufacturing GMH950453BX - 45,000...
Oct 26, 2011 | Goodman CKL24AR24 Air Conditioner
Apr 07, 2011 | Air Conditioners
Feb 16, 2011 | Air Conditioners
Dec 11, 2009 | Goodman Air Conditioners
Aug 18, 2009 | Goodman CLJ30AR32 Air Conditioner
Dec 05, 2008 | Goodman Air Conditioners
163 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: