Question about Heating & Cooling
If it needs a charge the leak has to be found and fixed. If the leak has been fixed and you have a service valve on the low side. It should have a vacuum pulled on the system to remove all air and non-condensable gases from the system. Then you can charge the system : 1. by weight according to the name plate. 2. charge by superheat (temperature leaving the evaporator + 16°F) When using the superheat method to charge the higher the Ambient temperature the lower the superheat difference will be.
Posted on May 01, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 10, 2014 | Coleman Mach III Air Conditioner
May 24, 2012 | Coleman Mach 3 Plus Roof Mount A/c Unit W/...
Jan 16, 2012 | Coleman Mach 15 Air Conditioner
Jul 31, 2010 | Coleman Mach 15 Air Conditioner
Jun 09, 2010 | Coleman Mach III Air Conditioner
Dec 06, 2009 | Coleman Heating & Cooling
Sep 09, 2009 | Coleman Mach III Air Conditioner
Aug 17, 2009 | Coleman Mach III Air Conditioner
Jun 29, 2008 | Coleman Mach III Air Conditioner
429 people viewed this question
Usually answered in minutes!