Question about Air Conditioners
If it needs a charge the leak has to be found and fixed. If the leak has been fixed and you have a service valve on the low side. It should have a vacuum pulled on the system to remove all air and non-condensable gases from the system. Then you can charge the system : 1. by weight according to the name plate. 2. charge by superheat (temperature leaving the evaporator + 16°F) When using the superheat method to charge the higher the Ambient temperature the lower the superheat difference will be.
Posted on May 01, 2008
Tips for a great answer:
Jul 21, 2014 | Coleman Air Conditioners
Jun 10, 2014 | Coleman Mach III Air Conditioner
May 24, 2012 | Coleman Mach 3 Plus Roof Mount A/c Unit W/...
Jan 16, 2012 | Coleman Mach 15 Air Conditioner
Jun 09, 2010 | Coleman Mach III Air Conditioner
Dec 06, 2009 | Coleman Air Conditioners
Sep 09, 2009 | Coleman Mach III Air Conditioner
Aug 17, 2009 | Coleman Mach III Air Conditioner
Jun 29, 2008 | Coleman Mach III Air Conditioner
428 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: