Question about Heating & Cooling
Look for signs of oil and you will have found the leak. Compressors depend on the cool gas returning to help cool the inner motor. At 12 pounds to recharge and leak detectors that measure less than .5 Oz per year leak rate does not figure that the leak can't be found.
10% of the oil from the compressor circulates with the refrigerant. The gas leaking will dissipate but the oil at the leak point will still be evident.
Posted on May 01, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 10, 2016 | Rheem 2.5 Ton 13 Seer Heat Pump -...
Dec 21, 2015 | Heating & Cooling
Dec 20, 2012 | Cars & Trucks
Since the failure of an air conditioner to turn on, loss of air conditioner cooling capacity, reduced air conditioning output temperatures, loss of cool air supply, or even loss of air flow entirely can be due to a variety of problems with one or more components of an air conditioner or air conditioning system, after reviewing the lost air conditioner cooling diagnosis procedures described in this article, be sure to also review the diagnostic procedures at each of the individual air conditioning diagnosis and repair major topics listed just below. To return to our air conditioning and refrigeration home page go to AIR CONDITIONING & HEAT PUMP SYSTEMS.
Electrical problems on HVAC systems: Keep in mind that despite the depth of technical detail you will find here about all components of air conditioners and heat pumps, most service calls for non-working air conditioners or heat pumps turn up an electrical problem. So if your A/C system is just not working at all be sure to check all of our electrical and control setting suggestions first.
Mechanical problems on HVAC systems: tend to fall into these groups: refrigerant leaks, dirty condenser coil or unit, dirty evaporator or cooling coil, or burned out (or hard-starting) compressor motors. We have also seen a number of problems with fans and fan motors in both the compressor/condenser unit and in the air handler/blower fan unit. Some of those fan problems are mechanical - like a loose fan belt or blade. MORE DETAILS
Nov 13, 2012 | Heating & Cooling
Mar 22, 2012 | Heating & Cooling
Jun 15, 2010 | Heating & Cooling
May 31, 2010 | Whirlwind FH-778 Air Conditioner
May 09, 2010 | Goodman CKL60AR60 Air Conditioner
Mar 16, 2010 | Goodman CKL60AR60 Air Conditioner
Jan 17, 2010 | Amana PTC153B50AM Split System Air...
109 people viewed this question
Usually answered in minutes!