Question about Ruud UBHC Air Conditioner
The unit is almost 3yrs old never had a problem. A few days ago, I noticed the thermostat display was off. The drain pan at the base of the indoor unit was full and the float valve shut off the system. I scooped out the water from the pan, filled the condensate pump tank and it worked fine. Water is still coming into both the pan and the small tank. What could be causing the water to bypass the pump tank?
That did the trick!!!
Posted on May 11, 2008
Blow out the drain line from the coil to the pump the clog is there causing the pan to fill up and trip off
Posted on May 10, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 30, 2013 | Heating & Cooling
Aug 18, 2011 | Carrier 38CKC036 Air Conditioner
Aug 09, 2011 | Ruud UBHC Air Conditioner
Feb 24, 2011 | Heating & Cooling
Sep 21, 2010 | Ruud UBHC Air Conditioner
Jul 03, 2010 | Ruud UBHC Air Conditioner
Aug 06, 2009 | Plumbing
Jul 04, 2009 | Ruud UBHC Air Conditioner
Apr 01, 2009 | Heating & Cooling
Jul 25, 2008 | Ruud Matching Split Air Conditioner
415 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: