Question about Whirlwind FH-778 Air Conditioner
Coleman central unit
You need to use a meter to ensure that you are getting control voltage from the xfrmr. Also check it at the coil side of the contactor if you feel comfortable doing this but be careful of the line voltage side. If you are getting power on the coil side of the contactor usually a 24v signal from the tstat from the area labeled y and the contactor is not pulling in most likely you will need to replace the contactor. If the contactor is pulling in verify the amp draw on the compressor with the tag.
Posted on May 30, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 24, 2015 | Coleman Heating & Cooling
Sep 06, 2012 | Coleman 15000 Btu Rv Roof Air Conditioner...
Jul 27, 2009 | Coleman Mach III Air Conditioner
Jun 29, 2009 | Coleman Mach 15 Air Conditioner
Apr 11, 2009 | Coleman Mach 15 Air Conditioner
Jul 11, 2008 | Coleman Heating & Cooling
Jun 05, 2008 | Heating & Cooling
Jun 04, 2008 | Coleman Mach III Air Conditioner
Jun 04, 2008 | Heating & Cooling
174 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: