Question about Goodman GPC1342H21A Air Conditioner
Check your crankcase heater. Likely on a temp sensor, only kicks on when temp drops to a certain point and when it does, trips the breaker.
Posted on Jul 19, 2017
Excessive current draw when motor first starts could and most likely does cause this breaker trip. I would check wiring connections to motor, check cold motor start up amperage draw, also breaker may be the issue (weak bimetal spring).
Posted on Jul 19, 2017
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If your outside condenser has a locked rotor or short circuit, than the unit WILL trip the breaker - as it should. On the other hand if a breaker is tripped a few times it will have less of a capacity that the rating, (this is designed in it). You will need to determine if the unit is locked (and broken) or the breaker has become too sensitive.
Posted on Apr 22, 2008
Whats the amp breaker? Is this for the inside unit or the outside condenser? If the inside and gas heat you have a bad fan motor, If its an electric furnace , the same, but if its the outside unit, the fan could be going bad, locking up and the compressor still runs and pulls high ampsand tripps breaker or the compressor is just pulling too many amps due to plugged coils with dirt , grass or weeds blocking airflow.(email@example.com)
Posted on Jun 09, 2008
SOURCE: Heat pump trips circuit breaker
i want to know the size of breaker to use.we are using a 30,30,30,30but it is kicking off.would a 40,40,40,40or higher be better if they sell them.
Posted on Nov 22, 2008
SOURCE: fan blows but not cold
possible breaker is bad. Have an electrician do an amp test on the compressor which will tell you if the compressor is bad. That is the only way to test the compressor. I would change the breaker first due to the age of the breaker and (if it hasn't been changed out before) due to the amount of time the breaker has ran your a/c system. I f this breaker continues to trip I would have the units compressor checked on amps being pulled from electric service
Posted on Jul 15, 2009
Tips for a great answer:
Nov 27, 2010 | Heating & Cooling
Jun 10, 2010 | Heating & Cooling
Feb 26, 2010 | Heating & Cooling
Sep 24, 2009 | Whirlpool Gold AD70USS 70 Pint Per Day...
Sep 20, 2009 | GE DBSR453EBWW Electric Dryer
Jun 30, 2009 | Dometic Rooftop RV Air Conditioner
Jun 15, 2009 | Heating & Cooling
Mar 19, 2009 | Refrigerators
Aug 22, 2008 | Whirlpool AD65USL / AD65USM Dehumidifier
67 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: