Question about Bryant Heating & Cooling
Is the compressor motor running? The compressor is a football-sized case with no apparent moving parts. It is located inside the air conditioner at the center. Is it humming or making any kind of continuous noise or causing the lights to dim? If it is making a continuous noise, and your air conditioner is still not cooling at all, there may be a serious problem with one or more of these areas: Compressor Condenser Evaporator These items are not user serviceable. You will need to contact a qualified appliance repair technician to repair these components. If the compressor is not running but you do have power to the air conditioner there may be a problem in one or more of these areas: Compressor Overload and/or relay Thermostat (Open thermostat) Burnt wiring Bad selector switch Capacitor.
The condensing coils will always be on the "warm" side of the air conditioner. That is, on the side that faces outside of the room to be cooled. Air is drawn into the back of the air conditioner on the sides through vent slots and is blown directly out through the condenser coils. If the coils get clogged with lint, dust and dirt the cooling system cannot provide the cooling necessary. To clean the coils it will be necessary to remove the entire cover of the air conditioner or pull it out of the wall to gain access to the coils. They can be cleaned by blowing compressed air at them or by using a soft bristle brush to wipe the dirt off. It is important to also clean any dirt or lint build-up in the bottom of the air conditioner so the condensate water will be picked up by the condensing fan slinger properly.
Posted on Aug 07, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
May 27, 2018 | Bryant Heating & Cooling
May 08, 2018 | Heating & Cooling
Aug 30, 2017 | Bryant Heating & Cooling
Aug 29, 2017 | Heating & Cooling
May 04, 2017 | Bryant Heating & Cooling
Apr 13, 2017 | LG Heating & Cooling
Mar 07, 2017 | Bryant Heating & Cooling
Jan 12, 2017 | Bryant Heating & Cooling
Sep 05, 2010 | Heating & Cooling
94 people viewed this question
Usually answered in minutes!