Question about General Electric 20 Amp, 1 Pole Thick Type THQL Ground Fault Interrupter Ge

# How many outlets will this carry? - General Electric 20 Amp, 1 Pole Thick Type THQL Ground Fault Interrupter Ge

Posted by on

• Level 3:

An expert who has achieved level 3 by getting 1000 points

All-Star:

An expert that got 10 achievements.

MVP:

An expert that got 5 achievements.

Vice President:

An expert whose answer got voted for 100 times.

• Master

While there is a practical limit for the number of outlets on a 15 or 20 amp general purpose lighting circuit in a _residence_, the National Electric Code (NEC) does not impose a # of outlets per circuit limit (residential ONLY).
However, some electrician's design general purpose lighting circuits in a residence using a point system. An outlet is 2 points and a light is 1 point. So, for a twenty amp circuit, (10 outlets x 2 points) = 20. Or, (5 outlets x 2 points) + (10 lights x 1 point) = 10 + 10 = 20. Or (8 outlets x 2 points) + (4 lights x 1 point) = 16 + 4 = 20. However you want to mix it up.

Now, if this is for a Commercial building, the the NEC allows no more than 180 VA (Volt Amps) per outlet. 180 VA / 120 Volts = 1.5 Amps.
20 amps / 1.5 Amps = 13.3 outlets. Drop the .3 and one determines that 13 outlets are allowed on a Commercial 20 amp circuit.

Also, if the 20 amp circuit is considered a continuous circuit (ON for more than 3 hours a day), then it can only be loaded to 80%. 80% of 20 amps = 16 amps.

Posted on Aug 08, 2010

Testimonial: "Thanks! That helps a lot..."

• Level 3:

An expert who has achieved level 3 by getting 1000 points

Superstar:

An expert that got 20 achievements.

All-Star:

An expert that got 10 achievements.

MVP:

An expert that got 5 achievements.

• Master

The reality is that a 20 amp circuit breaker itself does not determine much of anything except the wire gauge. You should use 12 gauge wire with a 20 amp breaker. That is because you want the breaker to always go first before the wire, so then a 20 amp breaker requires thicker wire then a 15 amp breaker.

As far as outlets, that depends on what you want to hook up and where.
If you have properly spread them out, you can hook up about 10 circuits to a 20 amp breaker. That is because most people do not use all rooms at once, so you can divide a breaker up into many different rooms at once, without risk of overload. This also has the advantage of making sure all the lights and sockets in a room do not go out with a single breaker, if there are more than one breaker to a room and each breaker goes to many rooms.
However, because it uses thicker wire, a 20 amp breaker is usually a specialty. It is used for large draws like refrigerator or microwave, and therefore may be hooked up to a single outlet.
It all depends.

Posted on Aug 09, 2010

Testimonial: "That's kind of what I thought. Thanks for verifying for me!"

Hi there,
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.

Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.

Here's a link to this great service

Good luck!

Posted on Jan 02, 2017

×

my-video-file.mp4

×

## Related Questions:

### My jnc660 wont charge

check the power outlet. check there is current at the cocket on the device. check the batteries and any fuses on the device itself if you have established that there is power coming to the end of the charging cable. Ensure that you are safe whilst carrying out the test procedure though, be systematic in your approach...i.e. check along the chain of supply.

Apr 23, 2016 | Cars & Trucks

### Dryer does not dry replaced element and it still does not dry

Please check your exhaust vent outlet that carries dryer exhaust (warm moist air) for blockage.

This blockage could be any where in the line from the dryer itself, in the line (s) or the outlet leaving the dwelling.

Please let me know if this is the problem, if not, then we will dig a little deeper!

Brian

Apr 14, 2008 | Dryers

### Do I need special electrical outlet?

You need to check with a licensed electrician for your area that would know the electrical codes. Most houses will all ready have an outlet for the stove and you will have to match it up with for the cord on your stove. Older homes that have not upgraded the electrical, typically will have a 3 wire outlet for the stove. Most newer homes, where the code requires, may have a 4 wire outlet. If you are replacing an existing stove I would recommend getting a new pigtail cord for the new stove so that you have new wires carrying the current instead of trusting old wires. Hope this helps!

Mar 20, 2015 | Ovens

### Why would two adjacent circuit breakers in a panel trip for no apparent reason? We reset them and everything seems normal.

My first thought is that even though it's only feeding that single outlet in the room; many times the neutral wires are made together in a panel (neutral/ground bar),which tries to carry the load of the initial tripped gfci. and tripping itself. Was there a decent amount of power plugged in to either the 'dedicated' outlet or the series of outlets that go to the 2nd breaker?

Jan 24, 2013 | Electrical Supplies

### Can u use 10-2 elect.wire to hook up power inverter in a car

Size 10 wire is pretty big - it will probably be too hard to use. How many amps do you plan to use? The #10 wire is good for 30 amps - that's usually more than what a normal house's outlet can carry. #14 wire can carry 15 amps.

Jan 13, 2013 | Heating & Cooling

### 30 amp rv outlet wiring diagram

Hot , Neutral & Ground, same as other household circuits, only heavier gauge wire to carry 30 amps, as well as 30 amp breaker in panel. Keep in mind, it is a 120VAC circuit, not 240VAC.

Dec 04, 2012 | Heating & Cooling

### How do I wire a Woods 59402 timer 240v input running two 120v outlets

Woods 59402 timer wires identical to Intermatic GM40, with same ratings and dip-switch settings.
http://waterheatertimer.org/How-to-wire-GM40-timer.html

Here is specific wiring diagram per your request, showing 240Volt input controlling two 120Volt outlets.
http://waterheatertimer.org/images/GM40-wiring-240v-120-volt-5.jpg
http://waterheatertimer.org/See-inside-main-breaker-box.html

Keep in mind that with 240Volt, both hot wires coming from breaker box carry 120Volt each, with 240Volt potential across both hot leads.
Each 120Volt Hot from breaker box, also carries 120Volt potential to Neutral or ground wire.
So the 240Volt wires from breaker box can supply the Hot for a 240Volt circuit, but the circuit must also have a neutral wire to complete 120Volt circuit.

Be mindful that timer is not 2-channel, so both outlets are controlled by same timing schedule.
If you want two different schedules for the outlets, then buy a 2-channel timer like Intermatic ET1125. Wiring for ET series remains similar to illustration link above.

If you need further help, I’m available over the phone at https://www.6ya.com/expert/gene_9f0ef4df2f9897e7

Dec 01, 2012 | Coleman Cable Woods 59402 40Amp Timer for...

### Switched AC Accessory Outlet no working

yes,go to a hardware store, but carry the one you get out of the unit.

Jan 18, 2012 | Harman Kardon AVR 225 Receiver

### How to install a electric line for over stove micowave

This is usually best left to a licensed electrician, however in some homes there is already electrical wiring over the stove for an exhaust fan. You might be able to tap into the exhaust fan wiring and install an outlet that you can plug the microwave into, or if there is an electrical outlet near the stove area you might can tap into it just be sure that you are not overloading the outlet. For example if there is a refrigerator or other major appliance using power from this outlet it might not carry enough current to operate the refrigerator and the microwave at the same time and will cause the circuit breaker to open or fuses to blow.

Sep 09, 2009 | Kenmore Microwave Ovens

### 2006 Eddie Bauer Explorer...the front charger / power outlet stopped working..rear one is just fine. Do you think blown fuse...my worr was that I thought they would be on the same fuse

they should be the same fuse. It could just be the front outlet is burnt out, auto part stores do carry replacements for most models that aren't too badly priced

Aug 31, 2009 | 2006 Ford Explorer

#### Related Topics:

370 people viewed this question

Level 3 Expert

Level 3 Expert