Question about Mastercool 67680 Evaporative Cooler Air Conditioner
If it was not drained for winter, do so and then remove all scale from the pan, pump inlet screen, etc. Replace the pads if they are scaled up and remove any scale from the louvered panels. WITH THE POWER OFF, check the belt for cracking and check to drive motor and blower wheel bearings for smooth operation, oil bearings with oil ports. With clean water in the sump, a good drive belt, clean pump screen and clean pads, the unit is ready to power up and run test the float action/shut-off, water distribution through the arms, belt tension (just enough to prevent slipping). These units work best when they can fully evaporate the water, so let the air flow out as fast as it come into the cooled space to maximize the evaporative effect. Also note, these unit must be level to work properly.
Posted on May 03, 2008
Where do I find the replacement pads for my Mastercool.
Posted on May 17, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 04, 2011 | Mastercool 67471 Evaporative Cooler Air...
Oct 10, 2010 | Mastercool 67471 Evaporative Cooler Air...
Jul 06, 2010 | Mastercool Portable Air Conditioner
May 09, 2010 | Mastercool 67680 Evaporative Cooler Air...
Feb 07, 2010 | Mastercool 67471 Evaporative Cooler Air...
May 12, 2009 | Heating & Cooling
Jan 27, 2009 | Mastercool 67471 Evaporative Cooler Air...
Jan 12, 2009 | Mastercool 67471 Evaporative Cooler Air...
715 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: