Question about Dometic Rooftop RV Air Conditioner
Yes, not good for compressor to stay on after being shut off, and hitting the breaker to stop it is a good idea. Sounds like you have a faulty/sticky relay. Not an expensive part, and shouldn't take any longer than 1/2 hr to change. Have a technician, or electrician look at it and give them a model number of unit so they can make sure they have a relay with them when they come. That way, another trip back, as well as a service charge will be eliminated. You have capacitors in the same area, that are very dangerous to work around if not experienced, so make sure the person is experienced, to avoid shock from 250-370 volts stored in those capacitors.
Posted on Aug 07, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 16, 2011 | Carrier Heating & Cooling
Jun 02, 2011 | Heating & Cooling
Sep 28, 2010 | Carrier Heating & Cooling
Jun 10, 2010 | Coleman Mach 15 Air Conditioner
May 31, 2009 | Fedders Vertical Chassis Air Conditioner...
Jul 12, 2008 | Fedders AEQ07FBG Air Conditioner
May 29, 2007 | Frigidaire FAS155K1 Air Conditioner
345 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: