Question about Heating & Cooling
Okay....two things to check on...
make sure that the terminals and the wires are matched in the t-stat and the furnace board...R-R Y-Y G-G W-W ....if everything matches up then you have a fried t-stat... What you are saying you have in the t-stat should be right... so it has to be one of these other scenario's...
Posted on Aug 07, 2010
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 03, 2015 | Heating & Cooling
Nov 15, 2014 | Heating & Cooling
Oct 25, 2013 | Heating & Cooling
Jan 25, 2013 | Heating & Cooling
Nov 29, 2010 | Coleman Heating & Cooling
Nov 01, 2010 | Heating & Cooling
Aug 04, 2010 | Coleman Heating & Cooling
Oct 28, 2008 | Coleman Heating & Cooling
May 30, 2008 | Heating & Cooling
Jan 21, 2018 | Heating & Cooling
Jan 21, 2018 | Dometic Heating & Cooling
119 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: