Question about Jandy Lite 2 Natural Gas Pilot Light Heater
Yes the repair men is correct.That this board blows at higher voltages.Many other users are too facing this problem.But if the unit is under warranty the Jandy company is really helpful and provides replacement in such cases.But if its out of warranty then getting the board replaced from local repair men is advisable,because company charges are very heavy for the same replacement procedure of board.
Posted on Aug 06, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 20, 2015 | Jandy Pool & Spa
Sep 15, 2014 | Jandy Laars Lite 2 Pool Heater 125,000 Btu...
So, you replaced part R367100 (Igniter)? This part if very susceptible to failure if touched. I would inspect and/or run a continuity check to make sure it has non cracks. Does it glow red when you attempt to start the heater? Remember, that is the how it ignites the flame, by getting red hot.
If it glows red hot, but does not light then I'd do the following testing in between;
Check that the inline fuses on the igniter aren't blown,
Check if the control board is sending a charge,
Check the flame sensor for gunk build up. Unfortunately to replace the flame sensor look like you have to purchase a whole new burner assembly to get a new flame sensor.
I also believe there is a toggle switch on the front door. It may need to be depressed before the system will ignite.
May 10, 2014 | Jandy Lite 2 Natural Gas Pilot Light...
Sep 28, 2012 | Jandy Lite 2 Natural Gas Pilot Light...
Igniter circuit is open. Check fuses on igniter wires. Identify and correct loose or broken wires.
Element has a fine crack in it. Replace
Igniter fault. Replace igniter.
Aug 31, 2011 | Jandy Lite 2 Natural Gas Pilot Light...
Jul 01, 2010 | Jandy Lite 2 Natural Gas Pilot Light...
Jul 10, 2009 | Jandy Laars Lite2 - 125,000 BTU Propane...
Jul 04, 2009 | Jandy Laars Lite2 Pool & Spa Heater -...
Sep 25, 2012 | Jandy Lite 2 Natural Gas Pilot Light...
58 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: