Question about Heating & Cooling
Check for power at the contactor. If no power there, check the circuit breaker, disconnect, or fuses. If there is power at the contactor, set the thermostat to call for a/c then check the contactor to see if it is pulled in. If it isn't check for 24vac at the contactor. If no 24vac then go to the thermostat and place a jumper between R and Y; that should make the contactor pull in if everything is good. If it does pull in when you install the jumper the problem is your thermostat. Let me know what you find.
Posted on Aug 06, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 08, 2010 | Haier hwr10xc6 Air Conditioner
May 03, 2010 | Amana PTH153B50AE Air Conditioner
Mar 28, 2010 | Craftsman 3 gal. Air Compressor, 1.5 hp,...
Jan 13, 2010 | Amana 22.6 cu. ft. Side-By-Side...
Oct 09, 2009 | Dewalt D55153R Reconditioned 1.1 HP...
Jul 30, 2009 | Goodman CLQ36AR49 Air Conditioner
Jul 27, 2008 | Intertherm Heating & Cooling
Jul 21, 2008 | Haier Heating & Cooling
57 people viewed this question
Usually answered in minutes!