Question about Goodman CPLE24-1 Air Conditioner
Set the thermostat so that the a/c should be on. Make sure you have 24vac at the contactor. If you don't recheck your wiring. Also you can go to the thermostat and install a jumper between R and Y. The contactor should pull in. If it does, your thermostat may be the problem. Let me know what you find so I can offer more advice.
Posted on Aug 06, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 07, 2018 | Coleman Heating & Cooling
Aug 30, 2014 | Coleman Mobile Modular Home Gas Furnace...
May 08, 2014 | Goodman Manufacturing Goodman GSC130421...
Jun 27, 2012 | Goodman Heating & Cooling
Feb 24, 2012 | Heating & Cooling
Feb 11, 2011 | Ruud UAKA042 Air Conditioner
Nov 01, 2010 | Heating & Cooling
Jan 09, 2010 | Heating & Cooling
May 15, 2009 | Heating & Cooling
352 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: