Question about Goodman CPLE24-1 Air Conditioner
Set the thermostat so that the a/c should be on. Make sure you have 24vac at the contactor. If you don't recheck your wiring. Also you can go to the thermostat and install a jumper between R and Y. The contactor should pull in. If it does, your thermostat may be the problem. Let me know what you find so I can offer more advice.
Posted on Aug 06, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 30, 2014 | Coleman Mobile Modular Home Gas Furnace...
on Aug 21, 2010 | Heating & Cooling
May 08, 2014 | Goodman Manufacturing Goodman GSC130421...
Jun 27, 2012 | Goodman Heating & Cooling
Feb 24, 2012 | Heating & Cooling
Feb 11, 2011 | Ruud UAKA042 Air Conditioner
Nov 01, 2010 | Heating & Cooling
Jan 09, 2010 | Heating & Cooling
Aug 09, 2009 | Heating & Cooling
May 15, 2009 | Heating & Cooling
232 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: