Question about Coleman Mach 15 Air Conditioner
I have a running fan, but no power to compressor,my thermo seems to be working corectely, and I need info on the relay in the box,as I,m gettig power to it, but it doesn't operate for power, and theother says NO??
On these relays NO means Normally open when power is not supplied on the control voltage side. Most A/C system control voltage is supplied by a transformer, which supplies the thermostat, which in turn supplies the power to the relay when cooling is called for. If you do have, say 24 Volts present at the relay the normally open contact should close giving power to the compressor for cooling. If the NO contact is not closing you relay coil may be open. In this case replace the relay.
Posted on May 11, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 09, 2013 | True THAC-48 48in Horizontal Air Curtain...
Oct 22, 2013 | Heating & Cooling
Feb 26, 2013 | Whirlpool Refrigerators
Jan 08, 2010 | Kenmore 53642 / 53644 Side by Side...
Oct 06, 2009 | Sanyo Heating & Cooling
Aug 06, 2009 | Amana Heating & Cooling
Oct 10, 2008 | 1990 Nissan Maxima
Jul 03, 2008 | Stainless Cruise 49 Marine Refridgerator -...
Aug 05, 2007 | LG DH30 GoldStar Dehumidifier
Jun 03, 2017 | Coleman Mach 15 Air Conditioner
73 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: