Question about Kitchen Ranges
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The problem is that the printed circuit board inside the generator draws a little current from the battery even when the generator is not running. Over the course of a few days this can make the battery weak enough to be unable to get recharged by the built in running charger which results in not enough power to run the electronic governor on the generator. Usually the spark plugs will work even with a fairly low battery.
Most of the Generac generators come with a built in trickle charger that runs off of the transfer switch load terminals. If your built in charger isn't doing the job it's either broken or you have the wrong sort of battery installed in the generator.
Posted on Jan 26, 2009
SOURCE: 10kw Generac shut down overspeed
Make sure that the throttle linkage is all there and not damaged/misadjusted, then get a manometer and check your inlet gas pressure. Gas pressure should be 8 inches of water column and stay there running or not.
Posted on Apr 06, 2009
Sounds like the electritian wired something wrong. Control wiring for that generator should be:
N1 and N2 = 240 vac utility input
Wire 0 = ground
Wire 194 (15B) = + battery
wire 23 = transfer signal
Posted on Oct 30, 2009
Yes,if its working correctly,you should be getting a reading about 2.5 to 3 volts above the battery voltage rating while its in standby mode.
Posted on Jan 17, 2010
Tips for a great answer:
Dec 12, 2015 | Generac GUARDIAN Standby Generator 10 kW/9...
Jan 28, 2015 | Generac 12kw Lp/ng Generator With Auto...
Jul 31, 2014 | Generac Power Systems Generac 0057500 75...
Jul 16, 2014 | Generac 5754 4.8 kW 120/240 Volt PrimePact...
Oct 01, 2012 | Generac Power Systems Generac 0057500 75...
Aug 25, 2010 | Generac HTSN100A 100Amp HTS 1ph 120/240V...
Aug 11, 2010 | Generac Guardian Series 5502 10 kW...
Jan 11, 2009 | Electrical Supplies
89 people viewed this question
Usually answered in minutes!