Question about Pentair Minimax NT Heater
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I am not sure if resetting the heater will work, or not, but it is worth a try! What you should do is open the right hand side door, find the POWER toggle switch and turn that off. Then find the Circuit Breaker for the heater and turn that off. Wait about 15 to 20 minutes, the reverse the order- Circuit breaker on, then the heater on. Try and start the heater.
If the error code comes back, check to see if there is glowing of the element. If not, turn over the Display Panel, there are Diagnostic Lights on the backside of the panel. If there is a light on next to a set of letters, that is whta is causing the issue with the heater.
Hope this helps!
Posted on Jul 13, 2009
This is a fan falure code. It can mean the fan has problems (not likley if the fan goes and isn't labored) You have a sensor in your exaust (probally not this if you don't get a good start) The culperet is probally in the negetive pressure sensor. This is a 2-3 inch disc with wires going to the controls and a rubber tube going to the fan. Pull the tube from the fan and make sure the fan fitting is clear (poke with a tooth pic) Be sure their are no kinks in the hose. If the heater is 4 years old the diaprahm could be bad in the pressure sensor. Check the other things first but this is probally your problem. Good luck, hope this helped.
Posted on Jan 26, 2010
This is an ignition flame falure code. Could be you don't have gas getting to the pilot, no spark to ignite the pilot or your ignition is not reading the flame. Sorry to say but it's probally time to get the pool guy out to look at it. Good luck.
Posted on Apr 15, 2010
Tips for a great answer:
May 06, 2016 | Sta Rite Sta-Rite Max-E-Therm High...
May 31, 2014 | Sta Rite Sta-Rite Max-E-Therm High...
Jul 11, 2017 | Pentair Mastertemp Heater
Jun 12, 2012 | Pentair Master Temp 300k Btu Natural Gas...
May 12, 2012 | Pentair Mastertemp Pool & Spa Heater Dual...
Apr 17, 2011 | Pentair MasterTemp 400000 BTU Pool and Spa...
Jun 30, 2017 | Pentair Minimax Ch 400,000 Btu Propane...
Jul 12, 2009 | Pentair Minimax NT Heater
195 people viewed this question
Usually answered in minutes!