Question about Coleman Mach 15 Air Conditioner
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
the fan motor bearings need lub....the shaft has a tiny access hole to put some oil into. because the fan shaft is slowing down, it is putting more strain on the voltage current, and eventually the internal breaker shuts down the ac........plus your condenser is not getting enough air accross it, compressor heats up, and it too will shut the unit down......older units have to be oiled every year, and eventually it too will fail, and a new blower motor assembly is needed or replace the ac unit.....blower motor units are around $130....now you install it or pay to have it done at around another $150 labor,,,,,try yourself, if it fails then call the tech........let me know ..ray..firstname.lastname@example.org
Posted on Dec 31, 2008
It probably has a clogged condensate drain. Take off the cover on top the RV and check hoses or tubes leaving unit for debris or lint. Often this water is used to help cool the condenser so look for leaves pine needles etc in the pan. There may be a cover you can remove on the evaporator section that will allow you to clean the collection pan and hose or trough. Is it possible the RV is far enough out of level that the condensate can't "run uphill"? Always power off while working on this unit unless you are electric savvy. Good luck!
Posted on Jun 28, 2009
The simplest answere to start is it' looks like the compressor is the ssue." Either it has siezed"or in my oppinion needs a proper household power to activate it. If the voltage drop on these units is a little below a certain value, it will not start and will burn out. Thats why i suggest a household power be tried first. I feel your generator is a little undersized. You will only know once you have applied household power.
Posted on Sep 23, 2009
Tips for a great answer:
Jul 12, 2015 | Coleman Heating & Cooling
Feb 01, 2013 | 1992 Chevrolet C1500
Aug 02, 2011 | Coleman Heating & Cooling
Feb 18, 2011 | 2001 Pontiac Grand Prix
Apr 14, 2009 | Coleman Mach III Air Conditioner
Jun 25, 2008 | Coleman Mach 15 Air Conditioner
Jun 11, 2008 | Heating & Cooling
May 20, 2008 | Coleman Mach 15 Air Conditioner
Jul 15, 2013 | Coleman Mach 15 Air Conditioner
49 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: