Question about Connecticut Electric THQP250 General Electric Packaged Circuit Breaker
These breakers are 1/2 size and only fit in an area of a panel designed for these. The bus bars must have extra tabs for these breakers. Before 2008 you could only have 42 breakers in a panel, so only some of the slots were reserved for these. Secondly, since this is a two pole 220breaker it must be in two spaces. This leaves a 1/2 space above and below the breaker. You could add a single pole breaker above and below. Now compare these in size, is there any way they can be as good as a full size breaker?
Posted on Aug 12, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 30, 2016 | Dell Computers & Internet
Mar 05, 2013 | Apex Digital DT250A Digital TV Converter...
Jun 26, 2011 | Avira AntiVir Personal - Free Antivirus
Jun 05, 2011 | One For All URC4220 Remote Control
Feb 07, 2011 | Sling Media The Slingbox Pro
May 14, 2010 | Canon PIXMA iP3300 InkJet Photo Printer
Jul 07, 2009 | Computers & Internet
Jan 15, 2009 | Cyberhome DVR 1600 DVD Recorder
Jan 03, 2009 | Toshiba RS-TX20
Sep 01, 2008 | Office Equipment & Supplies
Dec 11, 2017 | Electrical Supplies
77 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: