Question about Goodman CLQ30AR32 Air Conditioner
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
set the t-stat low and let it run for 5 minutes , stick a thermometer in the return air closest to the unit as possible until you get a good reading , then stick the thermometer in the cold air supply again closest to the indoor unit as possible let sit until it stops going down in temp.
this is called your temp difference and it should be atleast a 14deg. F difference from in to out. if its lower you have a refrigerant problem, Let me know how it goes.
Posted on Jun 10, 2009
Try using a garden hose to wash down the condensor coil (the coil that is exposed to the outside air).
During the cooler times when it seems to be working, check the temperature difference of the air coming out against the temperature of the air coming in (room temperature air). The temperature should be approximately 16 to 22degF difference. If you are not getting at least 16degF air, you most likely need to have your unit serviced to see if professionial cleaning or a recharge is needed. If you are getting the temperature difference but not getting the amount of cooling you need during hot weather, it could be a capacity problem. You can perform a quick test by using the calculator on this site:
I hope you find this information helpful. Good Luck! :-)
Posted on Mar 08, 2010
Here is a tip about trouble shooting your air conditioner...
Air Conditioner Trouble -Review the Possibilities
Posted on May 31, 2010
If properly charged your unit should perform fine, having a dirty condensor at that temperature can cause problems not easily recognized.
A well insulated house should be able to maintain a 20 degree temperature difference whether its summer
or winter. No Mechanical cooling or heating involved
for at least 6-8hrs if not more.
If it never cools when it is 95 degrees outside the ambient outside temperature is not the problem.
At 95 degree out side air you should be seeing inside discharge air temperatures betwenn 48-55 degrees.
It is the load in the house that determines how long the unit will run at 95 degress.
Posted on Jun 22, 2010
Tips for a great answer:
Jul 22, 2012 | Frigidaire FRA186MT2 Window Air...
Jul 22, 2011 | Daewoo Heating & Cooling
Jun 25, 2011 | Amana Heating & Cooling
Jun 19, 2011 | Friedrich ZStar ZQ10A Air Conditioner
Jul 20, 2010 | Whirlwind FH-778 Air Conditioner
Jun 28, 2010 | White Rodgers White-Rodgers 1F85RF-275...
Jun 21, 2010 | Goodman CKL24AR24 Air Conditioner
Mar 08, 2010 | LG Heat cool Window Air Conditioner
Jul 13, 2009 | Heating & Cooling
Jan 07, 2009 | Heating & Cooling
85 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: