Question about Heating & Cooling
Your "P" trap is plugged on your condensate line, is one possible problem. You will need to take the line off and clean the pipe then add evaporator drain tabs to your coils drain pan.
Posted on Apr 26, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 24, 2011 | Heating & Cooling
Jul 21, 2011 | Heating & Cooling
Jul 20, 2011 | Heating & Cooling
Jul 02, 2011 | Amcor Heating & Cooling
Jun 15, 2011 | Heating & Cooling
May 14, 2011 | Mitsubishi Heating & Cooling
Jan 01, 2011 | LG Heating & Cooling
Jun 02, 2010 | Coleman Mach 15 Air Conditioner
Jul 26, 2009 | Pelonis KCD-25YI Air Conditioner
Jul 22, 2009 | Royal Sovereign ARP-1000EX Portable Air...
363 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: