Question about Honeywell Heating & Cooling
This is more than likely the fan blower motor on the inside of the unit. You could get lucky enough to just have something get sucked into the return and has wrapped itself in the fan blades causing it to become off balanced, but most of the time it is either the motor bearings going out or the bracket that holds the motor in has broke. You can check any of these by shutting the power off to the unit and opening the blower motor compartment (usually just the front cover of the unit) and while the fan blade is no longer moving, and trust me, they can spin forever, feel around the blades to see if anything is in there and while your there, you can check the play in the wheel by grabbing it and try to moved it left to right. If there is play in the wheel, it will need to be taken out and either tightened back onto the shaft or the motor replaced. You can also check the bracket that holds the motor in, this should just be a visual check to see if any of them have broke or cracked. I hope this points you in the right direction and good luck!
Posted on Aug 05, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 29, 2011 | Sanyo Heating & Cooling
Aug 01, 2010 | Bryant 463AAC008BA Air Conditioner
May 08, 2010 | Weather King 12AJA4201AH Air Conditioner
Aug 27, 2009 | Ruud UAMB Air Conditioner
Aug 17, 2009 | Ruud Matching Split Air Conditioner
Apr 03, 2009 | HP Pavilion dv6000t Notebook
Feb 10, 2009 | Heating & Cooling
Feb 24, 2008 | Heating & Cooling
Oct 23, 2007 | Ruud UAMB Air Conditioner
79 people viewed this question
Usually answered in minutes!