Question about Heating & Cooling
That would be your indoor blower motor. It is either a bad motor or the capacitor is bad on it. Replacing them are never fun. The unit is freezing up because there is no air flow going across the evaporator coil when the outside unit is pumping refrigerant through the system. Hope this points you in the right direction!
Posted on Aug 05, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 17, 2017 | Heating & Cooling
Apr 19, 2016 | Heating & Cooling
Jun 15, 2014 | Goodman Heating & Cooling
Jun 13, 2010 | Bryant 463AAC005BA Air Conditioner
Aug 14, 2009 | Goodman CKL24AR24 Air Conditioner
May 25, 2009 | Goodman CKL24AR24 Air Conditioner
Jun 26, 2008 | Goodman CKL60AR60 Air Conditioner
Oct 26, 2007 | InFocus ScreenPlay 4805 Multimedia...
Jun 25, 2007 | Whirlpool ACQ158XP Wall/Window Air...
23 people viewed this question
Usually answered in minutes!