Question about Mitsubishi Mr. Slim MXZ30TN Air Conditioner
Check the following:
Make sure the filter and the evaporator coil are clean. Also check condenser coil in the outside unit is clean.
When unit is turned on there should be (on the led display, inside unit) one green light on for the blower and another one for the compressor, both lights should be ON untill the unit reaches the preset temp. If the light for the compressor (usually the light on the right side) does not stay ON, check the outside unit.
On the outside unit, check that when turned on, both the fan and the compressor kick in and stay running. If the fan motor stops, the compressor overheats and the thermal proteccion shuts it down to prevent damage. Also, if the R22 gas is low, the low pressure switch prevents the compressor from running.
Posted on Aug 04, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Mar 18, 2014 | Fujitsu Heating & Cooling
Apr 18, 2017 | Heating & Cooling
Dec 28, 2010 | Hitachi Heating & Cooling
Feb 14, 2018 | Goodman CLJ30AR32 Air Conditioner
Feb 15, 2010 | Heating & Cooling
Jul 13, 2009 | Heating & Cooling
Jun 23, 2009 | Honeywell Programmable Thermostat Heater
Apr 27, 2009 | GE AGQ10AJ Wall/Window Air Conditioner
Apr 26, 2009 | Heating & Cooling
287 people viewed this question
Usually answered in minutes!