Question about Dometic Rooftop RV Air Conditioner
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Recharge My AC Unit
The system needs to be accessed through what is call a tap valve. After a tap valve is in place a high vacuum should be pulled on the system down to 500 microns to remove air and non condensible gases along with any moisture from the system. Then the charge should be weight into the system according to the name plate with the proper type of refrigerant, generally Refrigerant 22. An alternate method is to charge the system by superheat of the gas returning to the compressor. Ambient temperature determines how high or low the superheat should be.
Posted on Jun 20, 2008
check the condensor fan in the rooof unit. It's the fan blowing on the cpil on the roof.. If it failed, the head preasures can becme excessive andwork the compressor hard causing the breaker to trip. Let me know and good luck, Ned_
Posted on Sep 13, 2009
Tips for a great answer:
Jul 10, 2015 | Coleman Heating & Cooling
Jul 18, 2011 | Coleman Heating & Cooling
Nov 14, 2010 | Dometic Rooftop RV Air Conditioner
Jul 08, 2010 | Dometic Rooftop RV Air Conditioner
Sep 19, 2009 | Dometic Rooftop RV Air Conditioner
Sep 14, 2009 | Coleman Mach III Air Conditioner
Jun 09, 2008 | Dometic Rooftop RV Air Conditioner
Jul 02, 2014 | Dometic Rooftop RV Air Conditioner
104 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: