Question about Pool & Spa
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Is there a coverplate where the wires come out of the pump? If so, remove the plate and there should be a wiring diagram inside.
Posted on Mar 18, 2009
Setting the pump for 115V wont by itself cause the trip. There is either a ground in the circuit or the GFI is bad. You may want an electrician to test any further than this.
Posted on Jul 04, 2009
You will need a two speed time clock to really take advantage of real energy efficiency savings. Intermatic makes one that fits in place of the original t104 time clock. You will need to run an additional wire to the pump as well. You will have the ground. Then one common wire that is always hot whether or not you are on high speed or low speed. You could make this a white wire. Then a black wire for your high speed that is energized in high speed and a red wire for the low speed. It is important that the high and low speeds not be energized at the same time, otherwise you will hear a very unpleasant sound coming from the motor, and failure and shortened life of the motor will be realized. HTH
Posted on May 29, 2010
Well first did you have an old one you're replacing? Check it. Second you could test your voltage with a tester (best idea then you know for sure). Third, you can look at the circuit breaker in your panel, and if it is a single breaker , it is 125V If it's a double pole breaker (two wide with wide handle) then it's 230V. Usually if it is 230V then the wires coming to it would both be black, or black and red, with a bare or green ground. Usually if it's 115V you'll have one black (hot), one white (neutral) and one bare or green(ground) but at times someone will wire one 230 with black and white. There should also be a large bonding copper jumper connected to a lug on the outside of the motor to bond your system to the pool (NOT AN EQUIPMENT GROUND)
Posted on Jul 05, 2010
Thank you for posting your question here on Fixya.com. If this answer does not fix your problem, please comment with additional details prior to rating the answer. Positive feedback is appreciated once your problem is solved!
There is no polarity associated with the leads in an AC system. You simply have 2 hot wires and you can hook either one to either Line 1 or Line 2. Motor rotation is not dictated by the connection arrangement of these leads. Ground the motor with the grounding wire and again with the bond wire if one is present.
You can remove the riser that is positioned under the motor to allow for a 56 size stator to fit in place of the 48 size stator the original Hayward (AOSmith) motor was.
Thank you for posting your question here on Fixya.com.
If this answer does not fix your problem, please comment with additional details prior to rating the answer. Positive feedback is appreciated once your problem is solved!
Posted on Nov 02, 2010
Tips for a great answer:
Nov 08, 2014 | AO Smith Pool & Spa
Sep 23, 2013 | AO Smith 1.5hp 1800RPM 56 Frame Farm Duty...
Sep 21, 2012 | AO Smith 1 hp 3450rpm 56Y Frame 115/230...
Aug 19, 2012 | A O Smith Motors A O Smith 1hp 115/230v Ur...
Aug 18, 2011 | Hayward 2HP Pool Pump Motor A O Smith...
Jun 03, 2011 | AO Smith 1 hp 3450rpm 56Y Frame 115/230...
Feb 06, 2011 | AO Smith 1 hp 3450rpm 56Y Frame 115/230...
Dec 14, 2017 | Pool & Spa
183 people viewed this question
Usually answered in minutes!