Question about Yamaha 2500 Watt Industrial Inverter Generator YG2800i
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
There was a day and time when generators were simple. There were no capacitors, regulators to control/adjust power to magnet or ground fault outlets. Winding getting hot indicates short, however could be bad capacitors. Rectifiers and capacitors must be removed from circuit to test properly. Here is a simple test that I use to find fault area. I use a small power supply (16v AC 1 amp like doorbell transformer) into the 110v outlet of generator. This should energize the armature magnet and actually produce voltage at commutator with brushes pulled off. You can slowly pull the starter rope to move the armature into a different positon the voltage will vary. If the ac windings are shorted there will be very little or no magnet. There is a seperate 110 v circuit at the 220v outlet to test (there are two 110v windings that make up the 220v outlet, one is also used for the 110v outlet). There is another winding that products voltage for the regulator that powers the magnet thru the brushes but I think that circuit is porbably working because of the heat in the windings. You might even have 110v power at the 220v outlet. As our parents told us over and over, be careful when working with electricity. Enjoy
Posted on Dec 08, 2008
the cap has to be disconnected on one side to get a true readingif you remove the cap from the system and check it again and find it out of range change it
the diodes should be checked also to make sure they are working ( the current should be going in one direction only on them) last check the recdifiers to see if they are all producing if one is out the voltage will be less
Posted on Mar 15, 2010
Tips for a great answer:
Mar 05, 2016 | Yamaha Ef600 Generator/inverter...
Dec 25, 2015 | Yamaha Electrical Supplies
Feb 15, 2015 | Yamaha Motorcycles
Aug 11, 2014 | Yamaha Ef600 Generator/inverter...
Sep 18, 2013 | Coleman Powermate Powermate 5000W...
Jul 24, 2011 | Yamaha 1,000 Watt Portable Generator...
Jan 15, 2010 | Yamaha 1,000 Watt Portable Generator...
Mar 28, 2009 | Electrical Supplies
Jan 27, 2012 | Yamaha 2500 Watt Industrial Inverter...
1,521 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: