Question about Heating & Cooling
Not heating - brings up E5 fault code on fairland unit. What does E5 indicate?
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: Fairland aircon error code
E-5 Outdoor activation of compressor over heatprotection or motor lock.
Check out door fan motor mechanism locked, replace motor. If less rpm replace capacitor. If condenser coil dusty, clean it. If no gas/short of gas, do leak test and rectify. Thanks.
Posted on Feb 08, 2011
Tips for a great answer:
Feb 08, 2011 | Heating & Cooling
Jan 05, 2011 | Heating & Cooling
Jun 24, 2010 | GE AJCQ08ACB Air Conditioner
Dec 10, 2009 | Heating & Cooling
Apr 01, 2009 | Carrier TSTATHPP 7-Day Programmable...
190 people viewed this question
Usually answered in minutes!