Question about Goodman Heating & Cooling
If your contactor is engaged, as it sounds like it is and you have 220 volts going out of it. Then the capacitor would be the device to look at next.
An ohm meter test on both sides of capacitor should show its condition. In your case I would guess the common terminal is bad (open).
There is another device added on to some units, this would be a time delay. Where it pauses up to 10 minutes before letting the compressor and fan start. This prevents short cycling. Carefully follow the wires to see if there is such a device between the contactor and main wires. If not then you are left with the capacitor again as the logical failed component.
Let me know if you have questions.
Posted on Aug 02, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 05, 2013 | Dometic Rooftop RV Air Conditioner
Aug 18, 2011 | Whynter Portable Air Conditioner
Aug 14, 2010 | Kenmore 72055 Air Conditioner
May 09, 2010 | Dometic Rooftop RV Air Conditioner
Jan 25, 2010 | Heating & Cooling
Jan 19, 2010 | Samsung AW0603B Air Conditioner
Jul 16, 2009 | Dometic Rooftop RV Air Conditioner
Jul 03, 2009 | Whirlwind FH-778 Air Conditioner
May 06, 2008 | Weather King 10AJA2501AH Air Conditioner
278 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: