Question about Lite On Laars Lite 2 Heaters: 250,000BTU MV Heater
Hi, on most all heaters you will have a chart somewhere on this unit, a code chart that will tell you what it means. It had to try and fire 3 times before it locked the module out do to a open safety switch, flame roll out switch, or a open pressure switch. Look, as they paste them on a panel or somewhere on the unit. If you have no luck, please use my user name below and I will look into it more for you. Send me all of the information to this unit. Keep me posted.
A/C, Heating, & Refrigeration Contractor
Posted on Aug 03, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Apr 20, 2018 | Cars & Trucks
Nov 04, 2014 | RTO Suburban Rv Water Heater Dsi Gas Valve...
Jul 16, 2014 | Lochinvar ENERGYRITE 150K BTU NATURAL GAS...
May 08, 2014 | Hayward 250kbtu Ng Pool Heater - Inground
Apr 17, 2011 | Heating & Cooling
Jan 10, 2009 | Goodman GDS81155CNA Open Flame Mid-Size...
630 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: