Question about Dometic 57915531 Air Conditioner
It should read 24v not 12v!!!!! Check your sub base on the t-stat. Voltmeter set on volts, touch R to C and get 24 volts if no common to the C then touch R to G which is the Indoor Fan Motor! If the Indoor fan is blowing air out the vents you are getting power to and through the transformer. AS stated check all wire connections and if good the problem is a faulty Contact Relay out side at the Condenser Unit! Check the low voltage wires comeing into it for 24v if it has it when the T-Stat is set to call for cooling then your contactor is bad!
Posted on Aug 22, 2010
If you don't here the compressor kick in after about 3 min then the thermastat is not telling the compressor to com on, or the control board is not telling the compressor to come on. The power can be traced from thermastat to the control board and will have a 12volt feed on the yellow wire at the control board with compressor mode on. From there it is 120volts the control board has a relay that turns on the compressor. the compressor capasiter can cause the compressor not to come on, normally it will have burnt wiring.
Posted on Aug 04, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 07, 2016 | Skyline 2013 Aljo GL Select Park Trailer...
Jul 07, 2010 | Kenmore 75085 Air Conditioner
Jun 09, 2010 | Heating & Cooling
Aug 11, 2009 | Sunpentown WA-1230E Air Conditioner
Jul 30, 2009 | Amana Heating & Cooling
Apr 18, 2009 | Westinghouse Refrigerators
137 people viewed this question
Usually answered in minutes!