Question about Nor-Lake KLF7766C Commercial Freezer
I would start there. If the thermostat has an off setting, turn it there and see if it goes off. If not, try turning it to it's warmest setting while the box is cold to see if it turns off. To test to see if the relay/ contactor is stuck/bad, kill power to the unit (Unplug or turn off breaker). Disconnect one wire to the thermostat. Restore power. If unit runs, bad relay/contactor. If unit does not run, I'd replace the thermostat. Make sure the sensing bulb of the thermostat is in the conditioned space of the box or in the return air (intake) side of the evap so it can sense the box temp.
Posted on Aug 21, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jul 08, 2018 | Freezers
Sep 28, 2011 | Magic Chef Chest Freezer MCCF5WBX
Sep 18, 2011 | Beverage-Air 44.9 cu. ft. / 1271 liter...
Jun 19, 2011 | Frigidaire 20.3 Cu. Ft. Frost-Free Upright...
Sep 07, 2010 | Freezers
Sep 01, 2010 | Turbo Air 23 cu. ft. / 651 liter...
Jun 21, 2010 | Frigidaire 20.6 cu. ft. / 583 liter...
Feb 24, 2010 | Frigidaire 20 cu. ft. / 566 liter Upright...
Aug 29, 2009 | Frigidaire 20.3 Cu. Ft. Frost-Free Upright...
Jun 24, 2017 | GE Freezers
252 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: