Question about APC Smart-UPS 3000VA UPS System
Hi, i'have an APC SmartUPS 300VA 220V (SUA3000I) that died due to lightning in the mountains.
i'm trying to repair it, but i need wiring diagram. do you have it?
i've not found a diode bridge, and i don't understand it.
The capacitor on 220V input C113 was broken.
The fuse (100A) on battery ground was broken also.
The rest of mainboard seems to be ok.
Can you help me, please?
APC do not release cct diags and these are not easy to repair, if the battery fuse was open and there is some board damage, the thing is toast. Even if you get it going the battery will not be able to be calibrated, unless there the board/processor is 100%, I know this as we have a similar model on the bench right now with new batts in and the unit will not recalibrate, so even though the batts are new, as soon as the mains is dropped it goes to very low battery and shuts down in 2 mins.
Buy a new UPS save yourself a lot of time. Hope this helps
Thanks for using FixYA
Posted on Aug 02, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 12, 2015 | APC Smart-UPS RT 3000VA UPS System
Jun 09, 2014 | APC SmartUPS VT 30kVA Rackmountable UPS ...
Feb 24, 2014 | APC Smart-UPS RT 3000VA UPS System
Sep 02, 2009 | APC Computers & Internet
Oct 23, 2017 | Odyssey Computers & Internet
463 people viewed this question
Usually answered in minutes!