Question about Goodman CKL60AR60 Air Conditioner
R22 boils and flashes from liquid to vapor inside the evaporator coil. This change of state happens at around 40 degrees. Any heat that is gained in the refrigerant from that point of 40 degrees is called SUPER HEAT!!!!! You want at least 10 degrees and not much more then 15 degrees by the time the refrigerant in its vapor state reaches the inlet line at the compressor! This translates to around 50 to 55 degrees as it enters the compressor. This temp relationship can be related directly to a corresponding pressure with a known refrigerant and a T/P Chart!
Posted on Aug 22, 2010
Hello my name is Heath it will be my pleasure to assist you. If you are talking about r-22 with an outside temperature of 75-80 degress farenheit it should be running between 62-68 on the low side and 200-225 on the high side but there are varibles to take into account like the air flow across the inside coil or a dirty evaporater just things to take into account these pressures are approximate if there are close it should be fine.
Posted on Aug 02, 2010
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 20, 2014 | Goodman CKL42AR42 Air Conditioner
Sep 02, 2013 | Goodman CKL60AR60 Air Conditioner
Aug 16, 2010 | Goodman CKL60AR60 Air Conditioner
Jul 07, 2010 | Goodman CKL60AR60 Air Conditioner
May 24, 2010 | Goodman CKL60AR60 Air Conditioner
Aug 12, 2009 | Goodman CKL60AR60 Air Conditioner
Jul 19, 2009 | Goodman CKL60AR60 Air Conditioner
Jul 29, 2008 | Goodman CKL60AR60 Air Conditioner
133 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: