Question about Goodman Heating & Cooling
Hi Jimmy, yes, I bet it is hot with that high humidity. From what you are saying, it sounds to me like this pusher switch is the contactor at the out door unit. It has the power lines going into it, and out the other side. It will have contacts on it that you can push down, is this what you are talking about when you say pusher switch? The indoor unit is 115 volts, you are right about that, but the outdoor unit contactor/pusher switch is 230 volts. You should have a box mounted by the outdoor unit for high voltage. Most all of the disconnect boxes have 2- 30 to 35 amp fuses inside them. You may not see them, so pull the plug and the plastic cover in the box to see if you have them. If you do, you may have blown a fuse. Replace both of them. This box is powered by a breaker at your main panel also. You will have a double pole breaker and make sure its not tripped. This contactor has a 24 volt coil on the bottom of it and is energized by the thermostat which closes the contacts to send power through to start the unit. You have to have 230 volts there. Turn the stat on cooling and go out to see if the pusher/contactor switch is energized. If so and the unit is not on, you have no high voltage there to run it, so check for fuses and the main breaker. You have power to the indoor unit, but not the out door unit. Start here and do these checks. Keep me posted on this Jimmy, and get back to me if this does not start the unit or if you trip a breaker. I will be watching for you. We will get it going. If this does the trick, be sure and rate me kindly as I know you will. Keep me updated by my user name below.
A/C, Heating, & Refrigeration Contractor.
Posted on Aug 02, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 12, 2014 | Heating & Cooling
May 11, 2014 | Dometic Rooftop RV Air Conditioner
Nov 01, 2010 | Goodman Heating & Cooling
Oct 19, 2010 | Heating & Cooling
Jun 27, 2010 | AcerPower 1000 (AP1000EA380M) PC Desktop
Jan 16, 2010 | AMD Codegen 350W ATX P4 Recommended...
Jan 15, 2010 | Omega Trane Furnace Draft Inducer Blower...
Jan 03, 2010 | Computers & Internet
Sep 30, 2009 | Dometic Rooftop RV Air Conditioner
Jul 08, 2009 | Dometic Rooftop RV Air Conditioner
53 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: