Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Compressor Fan stop working
Do you have a meter? Either the fan is bad or the capacitor is bad. Ohm out the fan and then the capacitor. Be sure you take the disconnect out of the electrical box on the side of the house and or trip the breaker off. The capacitor is a dual run one side operates the compressor and one side operates the fan. I would really bet on the capacitor being bad. Have seen that a lot in my experience. Be sure to make note of the wiring of the capacitor before you take it out to check and if you are not sure how to check it take it to the parts house and they can check it.
Posted on May 17, 2009
are you speaking of the outside fan or inside? compressor should be a little warm but not boiling hot. the unit could be low on freon. if low it will run a while but the compressor will overheat and shut off leaving the fan running by itself ouside. if nothing outside is running check power. if you have power check the contacted outside to make sure it's pulled in. contacters are bad about going out on goodman untis. Also ants can get under contacts.
Posted on Jun 18, 2009
your switch should be oopen but when it reaches 41 degrees it should open so the system shuts off before it damages the compresor by sludging it, i have the same unit and my compresor runs for 5 seconds and shuts off, i checked the amp draw at the compresor and it draws 21 22 amps trying to start after the initial 5 second run, but it wont come on againts a load so the comprresos equilizes and tries to start over again with out positive results. i bipass the external obverload on top of compresor terminals area, still no fix yet, the relay on the control board continious to send power to the compresor and still draws , so if there is a problem with the control relay i would open up and dont send power to the compresor so i dont think is the relay, i am a a/c service man for
35 years and do this for a living still today, by experience i think it is the compresor gone bad but will try by passing the relay just to see what happens, also it could be bad capacitor since it have a hard start relay and start capacitor (black )also a run (silver ) capacitor they check ok, there is no way to check the charge unles you install a saddle tap to check presures and rechage this unit i think the compresor replacement is the way to go ( around 250) plus labor and freon r22 e mail add firstname.lastname@example.org.
Posted on May 06, 2010
Tips for a great answer:
Jun 27, 2016 | 1998 Lincoln Navigator
Oct 15, 2015 | 2009 Hyundai Sonata
Aug 16, 2014 | 2008 Chrysler Sebring
Jun 20, 2012 | Air Conditioning and Heat for Pontiac...
Jul 01, 2011 | Whirlwind FH-778 Air Conditioner
Aug 11, 2009 | Heating & Cooling
Aug 02, 2009 | Heating & Cooling
May 10, 2009 | 1998 Dodge Durango
52 people viewed this question
Usually answered in minutes!