Question about Heating & Cooling
Does the compressor try to start and the shuts off or is the breaker slamming off as soon as it is turned on. If it takes a few seconds the comp could be locked up and trying to start, high amps and tripping breaker. Tripping breaker right now would indicate a shorted or grounded compressor. Really would need to be ohmed out with a meter to check for ground. Not good either way.
Posted on Apr 25, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 04, 2013 | Fisher and Paykel Washing Machines
Sep 11, 2011 | LG LSC121PMA Split System Air Conditioner
Jun 01, 2011 | AmcorAire UCHW-H12AF2 Split System Air...
May 10, 2011 | Heating & Cooling
Nov 28, 2009 | Coffee Makers & Espresso Machines
Sep 07, 2009 | Heating & Cooling
Feb 01, 2009 | Heating & Cooling
Dec 05, 2008 | GE Quiet-Aire Ductless Split System Air...
Mar 07, 2008 | Refrigerators
Oct 16, 2007 | Coleman Mach 15 Air Conditioner
199 people viewed this question
Usually answered in minutes!