Question about Goodman Heating & Cooling
Some things that would change air flow in a system are:
Blocked/Clogged Return Air. Usually a dirty filter.
Blocked/Clogged A-Coil. Inside the coil box, you have to remove the cover that is on the coil itself, unless it's a downflow, then you can see on top of the coil if it is clogged or dirty. You can usually clean it with a small wire brush.
Fan Settings Have Been Changed. On the electrical board inside the furnace, you will have terminals that your fan motor wires connect to. You should have a terminal for heat, one for cool, and two that are marked as "Park". The BLACK wire from the motor will be the highest speed setting. You will have this information on the schematics on the back of the furnace door panel also, they are fairly easy to read. All the speeds are HIGH/MED HIGH/MED LO/LOW. The two speeds you don't want, you place on the PARK terminals.
Furnace Blower Motor Getting Weak. If there seems like there is no change in the speed settings, then your motor could be going out and would have to be replaced.
These are just a few possibilities that you can check out. Hope it helps and good luck!
Posted on Aug 01, 2010
Testimonial: "I find this absolutely precious and am sure it will solve my problem. THANKS!"
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 16, 2011 | Dryers
Dec 24, 2010 | Kenmore 62802 Electric Dryer
Jul 23, 2010 | Carrier Heating & Cooling
Mar 03, 2010 | Dryers
Feb 14, 2010 | Heating & Cooling
Nov 19, 2009 | Heating & Cooling
Jul 30, 2009 | Jenn-Air JED8430 Electric Cooktop
Jun 24, 2009 | Heating & Cooling
Nov 20, 2008 | Frigidaire 30" Self-Cleaning Freestanding...
Nov 04, 2008 | Heating & Cooling
90 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: