Question about Goodman CKL60AR60 Air Conditioner
Find the rating tag on the motor for the centrifugal fan. Locate the FLA amp number! Using a clamp-on amp meter while the unit is at its full load running. Compare to the amp draw. If it is rated at say....FLA 28.6 amp and you take a reading of 16.2 or 23.1 then either the motor is failing or you are not getting proper supply voltage. Take a Volt reading of you supply voltage to insure there is enough voltage being supplied!
Posted on Aug 22, 2010
Inside the air handle there is a motor and a cage(squirrel). I am assuming this is the problem. The side that has the pilot light, take this cove off first, then the back cover. There is a switch so when you take the back cover off it opens the circuit. You will see a main board and to the left and behind is the motor and squirrel cage. I would kill power and then remove the bolts making sure I make the wires and where they go. Then just take the motor and cage out. You will need a allen wrench to remove cage, then replace motor. Hope this helps Tim
Posted on Aug 10, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 29, 2013 | Goodman Heating & Cooling
Jul 18, 2012 | Goodman Heating & Cooling
Jan 02, 2011 | Goodman CLJ30AR32 Air Conditioner
Jul 19, 2017 | Goodman Heating & Cooling
Aug 19, 2010 | Heating & Cooling
Aug 03, 2010 | Goodman Heating & Cooling
Jul 04, 2010 | GE AJCQ08ACB Air Conditioner
May 20, 2010 | Goodman CLQ36AR49 Air Conditioner
Mar 17, 2009 | Goodman Heating & Cooling
90 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: