Question about Goodman CKL42AR42 Air Conditioner
Either you have blown the low voltage fuse located inside the air handler (if there is one) or you have blown the transformer feeding the low voltage control wiring.
If the transformer is blown due to no fuse installed, I would recommend installing a low voltage 3A fuse in line with the red terminal coming off the transformer. This will protect the transformer in the future.
Posted on Aug 01, 2010
Testimonial: "Thanks, it was the transformer, and the AC tec added the fuse you recommended. Expensive!!"
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 06, 2011 | Goodman CKL36AR36 Air Conditioner
Aug 20, 2010 | Goodman Heating & Cooling
Jun 03, 2010 | Ruud UBHC Air Conditioner
May 24, 2010 | Heating & Cooling
May 21, 2010 | Heating & Cooling
Jun 24, 2009 | Goodman CLQ36AR49 Air Conditioner
Feb 11, 2009 | Heating & Cooling
385 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: