Question about Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
You need to call a reputable service technician. The freezing up usually is associated with a low refrigerant charge or low air flow. Check your return air filter and replace as needed.
Posted on May 30, 2009
When the unit is running, go outside and put your hand near the condenser fins, this air that comes out should be slightly warmer than the ambient temp. If it is not you will need to take the unit out of the window and out of its outer case and clean the condenser fins from the inside, this is no easy task as it is very hard to reach. You will want to get a small (toothbrushed sized) brass bristled brush with a long handle. Make sure the evaporator coil (in the front) recieves the same attention and wash the mesh filter that goes in front of the evaporator. Re- assemble and enjoy the cold air.
Posted on Jun 07, 2009
This unit is use in motels etc. Check the ouside coil ( conderser) from the inside (discharge fan ) for dirt. Most of these units are floor level . This can cause a unit to short cycle ( cold air is at the floor) .
Posted on Jul 18, 2009
Tips for a great answer:
Aug 28, 2017 | Heating & Cooling
May 25, 2015 | 2003 Ford ZX2
Jul 20, 2013 | Heating & Cooling
Apr 16, 2012 | Heating & Cooling
Jul 06, 2011 | Heating & Cooling
Apr 05, 2010 | Ruud Central System Air Conditioner
Nov 09, 2009 | Cell Phones
May 31, 2009 | Ruud UBHC Air Conditioner
Jul 30, 2008 | Heating & Cooling
87 people viewed this question
Usually answered in minutes!