Question about Heating & Cooling
Error U4 on your unit means Failure of transmission between indoor and outdoor unit.
the probable reasons for this would be
Indoor to outdoor, outdoor to outdoor transmission wiring F1, F2 disconnection, short circuit or
Outdoor unit power supply is OFF
System address doesn’t match
Defect of indoor unit PC board
Defect of outdoor unit PC board
to me it Sounds like an interconnecting wiring error. Check wiring connection i.e. wires are connected in right order 1 to1 2 to 2 etc. from indoor terminal board to outdoor terminal board. Also check for slack or loose connections.
However U4 code on the daikin means outdoor PCB is faulty and needs to be replaced.. and LED A not lighting also indicates faulty outoor pcb.
So give both the above conditions a check. you should be all set to go.....
Please please take necessary safety precaution before you try testing the unit yourself.... If you are least bit uncomfortable about what you are going to do... please do not hesitate to call for a technician.......
Good Luck with your fixya
Posted on Jul 31, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 29, 2008 | Heating & Cooling
Jan 03, 2015 | Heating & Cooling
May 04, 2013 | Daikin RXYMQ48MVJU, VRV-S Air Cooled Eight...
Sep 19, 2012 | Daikin Heating & Cooling
Feb 08, 2011 | Heating & Cooling
Dec 15, 2010 | Heating & Cooling
Nov 09, 2010 | Cfm Daikin R410a Split System Air...
May 28, 2010 | Cfm Daikin R410a Split System Air...
1,170 people viewed this question
Usually answered in minutes!