Question about Honeywell Air Conditioners
You could possibly have an ignition problem. The controller will go into a lock-out condition if flame is not established. Turning the temperature control down and then back up may be serving to reset the control system so it tries again.
Posted on May 22, 2008
I'm sorry to hear! On mine, another model of Burnham , there's a grey box (approx 4" high by 5" wide) on the front of the boiler. This cover slides off and the control settings are underneath. My manual says low limit must be 20 degrees below high limit else they will lock out each other. I find this to be the case when a maintenance man's "tuned" the settings. My manual also says to set the differential knob to 25 degrees. There are some manuals on the burnham.com site along with their phone number.
Posted on Jan 15, 2009
Tips for a great answer:
Nov 14, 2015 | Honeywell Air Conditioners
Sep 13, 2008 | Honeywell Air Conditioners
Jan 25, 2013 | Air Conditioners
Jul 04, 2011 | Air Conditioners
Apr 09, 2011 | Air Conditioners
Jan 06, 2009 | Air Conditioners
Nov 11, 2008 | Air Conditioners
Jun 08, 2008 | Honeywell Air Conditioners
May 21, 2008 | Honeywell Air Conditioners
202 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: