Question about GE Quiet-Aire Ductless Split System Air Conditioner AS1CD12AA0/AS0CD12AA0
You'll need to check the breaker to the unit to make sure you have power. If so, then remove the cover where your electical wiring enters the unit. There is a contactor that should be humming if it is recieveing a call from the indoor unit. If not, check the wires going to the unit for any damage. If you find the contactor you can manually press it in to check to see if it runs, if so, then it is a problem in the control wiring. or the control board inside is not sending the voltage out. You'll need a volt meeter to test this.
Posted on Jul 30, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jun 17, 2013 | Cars & Trucks
May 09, 2012 | 2007 Nissan Tiida 1.6
Aug 14, 2011 | Porter Cable C2002 150 Psi 6 Gal...
Aug 12, 2011 | Campbell Hausfeld 5 Peak / 1.7 Running HP,...
Jul 02, 2011 | 2002 Chevrolet Blazer
Jun 22, 2011 | Carrier 38CKC036 Air Conditioner
Sep 05, 2010 | Dometic Rooftop RV Air Conditioner
Jan 21, 2010 | Heating & Cooling
Dec 11, 2009 | 2003 Honda Civic
72 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: