Question about Heating & Cooling
My ac has quit coming on. When I looked inside the unit that sits outside, it looked like my contact switch was rusted and not working. I pushed down on the contact and the unit came on. So I held it down with a brick so that I could go inside and check on the air. It was blowing and was cold. So I thought the contact switch was bad and replaced it. It still will not come on by the thermostat. The thermostat partially works because the blower will come on and shut off by the setting but the compressor will not run by the thermostat. Is this simply a thermostat gone bad?
Thanks for any help.
Before you do anything check your overflo emergency switch!
Drain is stopped up causing switch to cut condenser off
Posted on Aug 19, 2008
Ok, do the following test:
take the cover of the thermostat and if you have a voltmeter put one lead on r and the other on y
if you have 24 volts low voltage is o.k.
now jump the r and y together and go outside if compressor turns on and runs wala! bad thermostat
now jump r and g if fan comes on fan relay's good
now check against any wiring diagram to see if any time delay device is installed for compressor
and if the unit has a circuit board, well the part that controls cooling went bad.
but if you have a fan relay installed and the fan goes on its o.k
any other questions e-mail me @ email@example.com
Posted on Apr 24, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Mar 23, 2015 | Ruud UAMB Air Conditioner
Aug 08, 2012 | Ruud Matching Split Air Conditioner
Aug 06, 2012 | Ruud UBHC Air Conditioner
Aug 14, 2010 | Ruud Central System Air Conditioner
Jul 08, 2010 | Frigidaire FAA065M7A Air Conditioner
May 16, 2010 | Ruud UBHC Air Conditioner
Jun 29, 2009 | Heating & Cooling
Jun 05, 2009 | Ruud UPMC036 Air Conditioner
Mar 19, 2009 | Ruud UBHC Air Conditioner
Aug 26, 2007 | Ruud UAKA037 Air Conditioner
193 people viewed this question
Usually answered in minutes!