Question about Carrier 38CKC036 Air Conditioner
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Central Air not cooling properly
This tubbing carries the refrigerant. The small line is flowing to their inside air handler. If the line is hot it is an indication that the outside unit is not able to release the heat. The most common reason is that the coil (looks like a car radiator) is dirty or plugged. This can be cleaned with a brush or sometimes a garden hose. They do make acid type cleaners for doing this, but the use of the acids are restricted in some areas.
By the way the other black pipe should have a larger copper line behind the black insulation. That line should be cold and sweaty like a nice glass of ice tea:)
Posted on Jun 26, 2008
Dear sir we need sugation for this we having prob with compressure Crrier Package unit model no : 50TJ16-028B/S We having little Diffreance with power supply (each phase.like a Red is 217v ,yellow is 218v Blue is 221v ) is there any problem for compressure .pls give me u r idea
Posted on Jun 15, 2009
it is fine and sounds like it is running at a high efficentcey. I wouldnt worry about it as long as it dosent cycle too much.
Posted on Aug 12, 2009
It sounds undercharged (needs more refrigerant). Based on the conditions in your post and assuming the indoor humidity is within 20-70% range, your target superheat should be 10degF. Your superheat (assuming you have an R22 system) is far too high. The pressures are not indicating a restriction; therefore, I have to conclude you have a low charge. A low charge will cause a gurgling sound due to the refrigerant in the liquid line is vaporizing prior to reaching the Cap tube at the Air Handler.
I hope you find this information helpful to you moving forward. :-)
Posted on May 10, 2010
Tips for a great answer:
Mar 07, 2016 | Heating & Cooling
Aug 05, 2015 | Heating & Cooling
Sep 11, 2010 | Heating & Cooling
Sep 03, 2010 | Goodman Heating & Cooling
Jul 02, 2010 | Weather King 10AJA6001AH Air Conditioner
May 10, 2010 | Heating & Cooling
Jan 31, 2010 | Hussmann Freezer Gelato Pan Rack (For 12...
Jul 28, 2009 | Heating & Cooling
Jul 03, 2009 | Heating & Cooling
Jun 13, 2009 | Ruud UAKA042 Air Conditioner
Jun 25, 2014 | Carrier 38CKC036 Air Conditioner
Jun 13, 2014 | Carrier 38CKC036 Air Conditioner
272 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: